- Our Story
Calculate Concentration for Glycol Freezing Point or Burst Point Protection
The required concentration of inhibited glycol needed in your system depends on the kind of cold weather protection that is needed. There are two basic protection points: Freeze Protection and Burst Protection.
What is Freezing Point Protection (Freeze Protection)?
Freeze protection is required in hydronic HVAC systems where fluid must continue pumping at the lowest anticipated temperature. This is in applications where no ice crystals can be permitted to form, or where there is inadequate space for expansion of an ice/slush mixture.
When we discuss freezing point protection, we are determining the coldest temperature at which the system fluid must continue functioning with little to no ice/slush mixture. We protect up to the lowest anticipated temperature (also known as the freezing point) by adjusting the antifreeze mix ratio, or the concentration of glycol in the heat transfer fluid. The higher the concentration, the colder the mixture will continue to protect.
Note that you should only protect up to the lowest anticipated temperature and no further, as there is a trade-off between efficiency and concentration. Excess concentration will impact maximum heat transfer efficiency.
Other appropriate applications for freeze protection would include:
What is Burst Point Protection (Burst Protection)?
Burst protection is sufficient if the hydronic HVAC system will remain dormant or inactive when the temperature drops below freezing and there is adequate space to accommodate the expansion of an ice/slush mixture. You may not be able to pump this slush, but your system will not burst.
When we discuss burst point protection, we are determining the coldest temperature at which the system fluids will become ice/slush, but doesn’t freeze and expand enough to burst the piping and coils. We protect up to the lowest anticipated temperature (also known as the burst point) by adjusting the antifreeze mix ratio, or the concentration of glycol in the heat transfer fluid. The higher the concentration, the colder the mixture will provide protection.
Glycol Calculator: Determine Required Concentration for Cold Weather Protection
Use our Concentration Calculator to determine the required concentration of inhibited glycol fluid needed for your desired cold weather protection. You will also find below a chart showing concentrations of glycol fluids required to provide freeze and burst protection (also known as an antifreeze temperature chart, burst and freeze protection chart or glycol concentration chart). The calculator and the chart provide the same information, just displayed in different ways!
Propylene Glycol Freeze Chart
Ethylene Glycol Freeze Chart